FTS delivered and installed a portable mix kitchen complete with ventilation system, sump containment, and a dry chemical fire suppression system. Within the paint kitchen we installed components that would allow for six 55-gallon drums of different color resins, and one 55 gallon drum of solvent. Stainless steel circulation lines were plumbed from the paint kitchen to the spray cell with all necessary ball valves, fluid regulators, spray guns and hoses also included. A load cell liquid level monitoring systems was installed to provide visual information as to drum capacity as well as audible alarms for low levels. All of the systems were pressure tested with air, then flushed with a compatible purge agent and finally filled with paint. The system was designed, built, and verified to meet all applicable OSHA and NFPA requirements.
The project which included six paint circulation systems, one mold release and one solvent purge system, was designed, built, and installed in 12 weeks.
Build - Paint Kitchen Enclosure
Assembly - Peripheral Equipment and Components
Delivery and Installation
Overall Part Dimensions:
Number of Colors
(4) 55 gallon drums of resins and (1) Catalyst
Number of Solvents
(1) 55 gallon drum of solvent
(2) Sets of double doors with ramps for easy entry and exit.
For worker safety and fume evacuation.
(2) Explosion proof lights provided.
Static electricity bonding system with grounding lugs.
Sprinkler heads with exterior connection adapter in accordance with NFPA-30.
Nema enclosure for lights, motor starter, fan and fire suppression interlock switch.
In process testing/inspection performed:
Industry for Use: